Understanding Ultraviolet System in Water Treatment
Ultraviolet germicidal irradiation (UVGI) is a disinfection method that uses ultraviolet (UV) light at sufficiently short wavelength to kill microorganisms. It is used in a variety of applications, such as food, air, and water purification. UVGI utilizes short-wavelength ultraviolet radiation (UV-C) that is harmful to microorganisms. It is effective in destroying the nucleic acids in these organisms so that their DNA is disrupted by the UV radiation, leaving them unable to perform vital cellular functions.
UV water treatment devices can be used for well water and surface water disinfection. UV treatment compares favorably with other water disinfection systems in terms of cost, labor, and the need for technically trained personnel for operation: deep tube wells fitted with hand pumps, while perhaps the simplest to operate, require expensive drilling rigs, are immobile sources, and often produce hard water that is found distasteful. Chlorine disinfection treats larger organisms and offers residual disinfection, but these systems are expensive because they need special operator training and a steady supply of a potentially hazardous material. Finally, boiling water over a cook stove is the most reliable treatment method but it demands labor, and imposes a high economic cost. UV treatment is rapid and, in terms of primary energy use, approximately 20,000 times more efficient than boiling.
UV disinfection is most effective for treating a high-clarity, purified reverse osmosis distilled water. Suspended particles are a problem because microorganisms buried within particles are shielded from the UV light and pass through the unit unaffected. However, UV systems can be coupled with a pre-filter to remove those larger organisms that would otherwise pass through the UV system unaffected. The pre-filter also clarifies the water to improve light transmittance and therefore UV dose throughout the entire water column. Another key factor of UV water treatment is the flow rate – if the flow is too high, water will pass through without sufficient UV exposure. If the flow is too low, heat may build up and damage the UV lamp.
A disadvantage of the technique is that water treated by chlorination is resistant to reinfection, where UVGI water must be transported and delivered in such a way as to avoid contamination.
It used to be thought that UV disinfection was more effective for bacteria and viruses, which have more exposed genetic material, than for larger pathogens that have outer coatings or that form cyst states (e.g., Giardia) that shield their DNA from the UV light. However, it was recently discovered that ultraviolet radiation can be somewhat effective for treating the microorganism
Cryptosporidium. The findings resulted in the use of UV radiation as a viable method to treat drinking water. Giardia in turn has been shown to be very susceptible to UV-C when the tests were based on infectivity rather than excystation. It has been found that protists are able to survive high. UV-C doses but are sterilized at low doses.
UV system must be worked together will a good pre filtration system in order to purified the particles, sediments and others chemical contaminants. For more information about UV system water treatment or UV purifier, please email to us on firstname.lastname@example.org or call us at